How to solve the problem of water leakage of chiller 10kw?
The water leakage at the inlet and outlet of the GX/GY -65°C ~ -10°C Industrial Refrigerators is usually caused by loose or broken bolts at the connection, which can be repaired or replaced.
There is water leakage at the float valve of the refrigerator. The float valve controls the opening and closing of the inlet valve according to the buoyancy. The solution is to check and adjust the position of the ball valve. If it is damaged, it should be replaced and repaired in time.
If there is water leakage in the evaporator shell of the refrigerator, check whether there is water leakage at the welding part of the evaporator shell. If there is any, weld and repair it as soon as possible;
The internal condenser of the refrigerator has water leakage due to perforation. The solution is to find the fault point and repair it.
The water in the water tank of the refrigerator is too full, which causes the cooling water to fluctuate and leak during operation. The solution is to reduce the water level in the water tank.
There is water leakage in the water tank of the refrigerator. There may be trachoma in the welding position of the water tank or it has been used for a long time. The solution is to pull it back to the manufacturer and re-weld the water leakage position.
The water leakage of the refrigerator water pump may be caused by poor connection of the shaft seal at the water pump or damaged shaft seal. The solution is to directly replace the pump without replacing the shaft seal.
If the refrigerator is tilted for a long time, it will lead to uneven stress on the valve, pipeline and other parts of the refrigerator, which will cause damage and water leakage. The refrigerator should be placed horizontally according to the specifications.
1. Refrigerator insulation material selection.
The selection of thermal insulation materials should first consider the temperature range of the equipment. Flame retardant materials must be selected. The temperature range of thermal insulation materials should include the temperature range of the equipment, with a margin of more than 30 ℃.
When users ignore this problem, it may cause fire. The thermal insulation material shall be wrapped in sufficient quantity, otherwise the equipment control may not reach the expected effect.
2. What is the function of the refrigerator?
The chiller unit provides cooling. They use air, water or evaporation. First of all, you need air chiller, water chiller or evaporative chiller, which depends on the building type and technology.