Direct cooling type low temperature refrigeration equipment
The refrigerant in the refrigeration system is directly output and evaporated into the target control element (heat exchanger) for heat exchange, thereby cooling the target control object. The heat exchange capacity is generally more than 5 times higher than the heat exchange capacity of the fluid (gas) transported into the heat exchanger. This is especially suitable for applications where the heat exchange area of the heat exchanger is small but the heat exchange capacity is large. It can also be used as a gas trap. The refrigerant is directly passed into the trap to evaporate, and the gas in the space can be quickly trapped through the condensation effect of the trap surface.
Product Parameters (All products can be customized)
|Temperature control accuracy||±0.5℃ control evaporation temperature|
|Throttling method||Electronic expansion valve|
|Show record||7-inch touch screen, record temperature, system pressure and other information|
|Main components||Danfoss filter drier, Castor solenoid valve, Johnson Controls pressure sensor, EBM fan (air-cooled), Danfoss/Emerson oil separator,|
|Compressor||Secop, Taikang, Emerson, Carlisle|
|Refrigerant||R404A Optional R507C R448|
|High temperature cooling||With 150 degrees high temperature direct cooling technology, to meet the goal of rapid cooling ability during high temperature operation|
|Power supply V||380V 50HZ|
LNEYA attends various exhibitions at home and abroad every year. At the exhibition, we show the latest research equipment of LNEYA. Every year, long-term cooperative customers will come to exhibitions and communicate with us. We are also actively developing new customers to provide them with high quality machines and services.
After sale service
Guarantee that the goods are sold to be conform to the provisions of the contract and qualified new products by factory inspection, quality performance, technical indicators and configured are in accordance with manufactures and technical documents stipulated in the contract.
Installation and debugging
After the arrival of the goods, my company or my company agent is responsible for installation and debugging of equipment need on-site installation and debugging.
Inspection and acceptance
After installation and debugging, acceptance by the customer to confirm the goods to be conform to the provisions of the contract and qualified new products, quality performance, technical indicators and configured are in accordance with manufactures and technical documents stipulated in the contract, and after the confirmation of a full set of technical documents, sign the installation acceptance report and confirm acceptance.
At the same time of installation and debugging of equipment, my company’s after-sales service engineer is responsible for technical training for user until user can be skilled of operation. In the process of using equipment by customer, customer can consult relevant technical issues to after-sales service personal of our company at any time, according to the situation, my company will arrange training on site or remote.
After sale service commitment
A full free one year warranty since the date of acceptance, during the warranty period, all repairs and spare parts are free of charge(instrukent malfunction caused bu human factors will be charged of cost price of spare parts); After the warranty period, we will be responsible for maintenance of equipment for lifetime, according to the actual maintenance fees, appropriate fee will be charged.
(PS:There will have extra charge if the customer need on-site service. And customers need to describe the issue first and then send some failed pics or videos in advance, then Lneya judge if it is possible to go for after-Sales on site. )